$125 Order Minimum Total Required!
In the M5602-7808-1, downward switch height adjustment by the end user can be as much as 2", and an upward adjustment can be as much as 9". This would allow a series of tanks to use the same level switch configuration and provide easier field adjustments for low level indication. Multi-level indications can also be provided.
The adjustment is done by loosening the compression fitting on the top of the 2" NPT pipe plug and moving the entire stem up or down as needed in the application. The M5602-7808-x series is supplied with Teflon ferrules in the compression fitting. These types of ferrules allow the end user to adjust the length multiple times. The retaining rings are not to be moved, unless the operation needs to be changed from Normally Closed to Normally Open.
Common level switches allow end user to adjust switch depth or height
Can overcome uneven tank stands to allow for accurate low level indication
User can change operation from Normally Closed to Normally Open
Engineered configurations available
Note: SPST = Single Pole, Single Throw
Switches are rated for resistive loads. See our Electrical Considerations for UL guidelines for current (Amperes resistive) at different voltages.
|Type||Full-Size Adjustable Length Switch|
|Stem Material||316 Stainless Steel|
|Float Material||316 Stainless Steel Float, with PH-15-7 MO Stainless Steel Retaining Clips, Not For Use in Salts!|
|Max. Temperature||392˚F (200˚C)|
|Fitting Type||2" NPT Pipe Plug with Compression Fitting for Adjustability|
|Max. Pressure||105 PSIG|
|Switch Rating||60 Watt, 240V max. (AC/DC), SPST|
|Lead Wires||72", 22 AWG, 2 Conductor, Teflon Jacketed Cable (Standard)|
|Approvals||CE, UL, CSA|
|Operation||Normally Closed, opens on rising level. User can reverse operation|
|Level 1||10.5" ± 0.125"|
|AC Voltage||60 VA Nominal - 0.50 amps max. @ 120 VAC, ( 0.40 amps @ 240 VAC)|
|DC Voltage||60 W Nominal - 0.50 amps max @ 24 VDC, ( 0.20 amps @ 120VDC)|
|Note 1||Switches are rated for resistive loads. See our Electrical Considerations for UL guidelines for current (Amperes resistive) at different voltages.|
|Note 3||Retaining rings are PH-15-7 Mo Stainless Steel and are not to be used in salts|
Contact Madison Co. if you have technical questions or need additional information not displayed here. Call - 203 488 4477